Question about Intertherm P3RA-048K Air Conditioner
Yesterday the coils on the indoor indoor unit froze up. I turned it off and let it thaw out, I tried running it again for a short time and noticed the coils were starting to freeze up again. what could the problem be?
You have a low refrigerant (leak) problem or poor airflow due to dirty coils or bad fan motor.
Maybe a combination of all 3.
Check the coils for dirt and lint. Check the fan motor blower wheel for lint on the blades. Check the condensing unit refrrigerant operating pressure. Low side for R22 should be approximately 68 psi, R410 pressure should be approximately 135 psi.
Posted on Sep 28, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
on Jan 03, 2010 | Heating & Cooling
Jun 23, 2015 | Norpole 5000BTU Mechanical Window Air...
Sep 01, 2014 | Heating & Cooling
Aug 30, 2011 | Haier Heating & Cooling
Aug 07, 2011 | LG LWHD1009R Air Conditioner
Aug 02, 2011 | Heating & Cooling
Jun 23, 2011 | Heating & Cooling
Jun 28, 2009 | Carrier 38CKC030 Air Conditioner
255 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: