Question about Hayward H Series Induced Draft Abg 100,000 Heater
I've jumped out all of the safetys and the same thing happens.
Hayward model H1001D
You may have spider webs in the gas orfaces. Pull the tray and unscrew the orfaces from the gas manifold then clean with a toothpic or the like, These will be very small webs and are hard to see but they dirvert gas from the burner with the ignitor and when it does light the ignitor can't reconigse the flame and it will go out. i've seen this happen after the heater is off for the summer season and I've seen it happen ovet night. This iss one of the things you can avoide by cleaning and serviceing the heater once a year. i hope this was a help.Good luck
Posted on Oct 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 29, 2017 | Pool & Spa
Aug 05, 2012 | Hayward Pool & Spa
Apr 24, 2011 | Hayward H-series Electronic Gas Pool...
Sep 21, 2009 | Hayward H Series
Aug 03, 2009 | Hayward H Series
May 28, 2009 | Hayward H Series Pool & Spa Heater 400k...
552 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: