Question about Hampton Bay 52 In. Black Huntington III with Quick Install Fan
I just replaced a ceiling fan (with light) with a new light (no fan)...Now the light will not turn off from the switch. I only have 2 white and two black and ground coming into box. But i have 3 separate switches that work the same light. What could be wrong?
One of the two cables in the ceiling box is power and the opther is a switch leg .. what you need to do is connect the two black wires together at the ceiling, connect the white power wire to the white fixture wire ,.,. connect the white switch wire to the black fixture wire .. put some black tape on that white to make it legal .
Posted on May 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 21, 2016 | Hampton Bay Dryers
Mar 23, 2015 | Dryers
Sep 29, 2014 | Dryers
May 26, 2014 | Computers & Internet
Oct 05, 2011 | Hampton Bay 52 In. White Redington...
Apr 22, 2011 | Aloha Housewares (93645) Ceiling Fan
Jul 21, 2010 | Hampton Bay 24750 Huntington III Ceiling...
Mar 23, 2010 | Hunter 52" Ceiling Fan With Light And...
Nov 25, 2008 | Hampton Bay 24750 Huntington III Ceiling...
Sep 25, 2008 | Dryers
121 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: