# 2 12/2AWG = 1 10/3AWG

Moving electric dryer w/ 4 wire receptacle and need to run 220v 30amp circuit to it. I have several possible routes to the main, the shortest- about 30' isthe most difficult to ''thread'' , the easy way is maybe 70'. 2 questions
:
1. what wire AWG does code call for either length run?
2. If 10/3 is needed, can one circuit using double run of 12/2AWG safely provide the same 220V service as single run of 10/3AWG to that 4 wire receptacle?

Thanks
Keith

Posted by on

• CaptKoKo Sep 27, 2009

Please clarify, given with 12/2 w/ground I have a Black, a White and a bare ground wire in each cable. I use two 12/2 blacks for one hot phase, two 12/2 whites for the red hot phase, one ground wire for the white neutral and one ground wire for ground. Is this OK?

kk

• CaptKoKo Sep 28, 2009

I am confused. each 12/2 w/ground has 3 wire. Times 2 is 6 total. 2 black, 2 white(now red) and 2 ground. The circuit breaker is a single 2 pole 30amp breaker, to use with 220VAC circuit I have the 2 blacks-as one- going to one pole of the breaker and the red(2 whites as one) going to the other - so much for the two hot phases. OK?
Now the two ground wires. Do both go to ground? or one to neutral and one to ground? Is a single 12AWG wire adequate for neutral and a single 12AWG adequate for grounding a 220 circuit?

×

• Level 3:

An expert who has achieved level 3 by getting 1000 points

All-Star:

An expert that got 10 achievements.

MVP:

An expert that got 5 achievements.

President:

An expert whose answer got voted for 500 times.

• Master

Yes, with a double run of 12-2w/ground you'll end up with 2pairs of 12 for your 2 hot phases(you will need to mark one pair red to substantiate the 2 different phases) and each 12 gauge wire will carry 20 amp each alone, then you'll have 2 pairs of 12 with white insulation white for neutral is fine but the other pair for the safety ground will need to be marked or painted green where ever visible per N.E.C. i.e. main panel or dryer receptacle or hardwired into the unit itself,use 10-3w/ground its cheaper in the long run and you dont have to run a doubleheader

Posted on Sep 27, 2009

Testimonial: "dmftrucker was patient with me... it took a bit for all to sink in but I got good technical, code based advise from him. Thanks a Lot! kk"

• daniel hendrickson Sep 27, 2009

yes all you need to do is make sure that where ever the whites are used as safety ground mark it with green tape, as for the other BLACK phase that I suggested marking one pair of the 2 pair red, you do not have to, its just a common courtesy, and as a reminder that its a 240 volt phase wire, but your not obligated to,if you use 10-3 W/Ground you dont have to worry about this step its there already inside the cable jacket....just make SURE the 2 wires that you are going to make your safety ground are marked,painted,or taped GREEN...as this is an N.E.C. code requirement!!!

• daniel hendrickson Sep 28, 2009

that would work, but by new N.E.C. reg your neutral must be insulated also, and your one insulated conductor short, as using 2-12 insulated per phase for 4 wires then one more insulated white for the neutral which you could get by with due to "derating" the neutral because it only carries the un-balance of the current, but keith i still think you should go with 10-3W/ground then each hot single hot is good for 30 amp,also your neutral is good for the same, and your ground is in the same jacket all in one wire and its not that much more expensive,especially in labor savings by running only one wire to accomplish this and your neutral isn't "derated"

×

Hi,
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
Goodluck!

Posted on Jan 02, 2017

×

my-video-file.mp4

×

## Related Questions:

### I have a 440v 50 amp and a 220v 30amp main breaker box outside my house. the 440 goez to the inside of the house and i have to unplug the 440 and plug in myown 440 plug i connected to another breaker box...

Some of these numbers don't make sense?
I have Never heard of 440v and 220v in a residential application, they are two different systems, 480 volt is typically 3 phase power, and 240v is typically single phase, more in likely you have a 200- 400 amp main service, and a 100- 200 amp secondary service for the welder, that can't be 110 @ 200 amps?
I would need more info, and pictures of actual nameplates of the equipment,

Mar 17, 2015 | Electrical Supplies

### Dryer will not dry clothes.

I assume it runs and this is from that stance. If it doesn't the motor has to be checked and the power coming in. In fact the dryer can run and still not have the correct power to opperate the heater.

Assuming you have a volt meter and know how to use it properly.

These are the steps that the power and machine have to take to operate properly

A. If the dryer has all of these things it has to be heating and an air flow problem (kinked or dirty dryer duck, motor fan clogged with lint, vent flapper not opening...) is suspect.

B. ELECTRICAL
1. power is correct (USA 220V across line and 115v to ground/neut) 2 hot lines with potential between them and a neutral and possible a ground
2 Door switch is closed
3 Timer switch closes and ready s power to heating element through centrifugal switch in the motor circuit after the motor is running.
4 the heating element is assumed to be good and have 220v at this point. Checking for voltage at the element will assure all before are ok and at least allowing the heater to work.
5 the heating element is controlled by 1 or more thermostats and a safety thermostat. If either of these switches do not close when the dryer is "cool" they are bad. NOTE some dryers could ahve 3 wire thermostats. These can read closed on one set and open on the other. And this is how they should be if good. But tracing the wire diagram will tell which set is closed and when.
6 if you have power, the timer contacts to the motor and the heater (separate circuits usually)are "closed", the motor runs, the cent switch "closes", the temperature operating thermostats are closed, and the heating element is good you have to have heat.

1 Check for 220V power into the dryer. If not check breakers and turn off and on several time pushing them firmly. If this is ok and 220V present step 1 is done.

2 This assumes the motor will run

Nov 01, 2010 | Whirlpool LER4634J Electric Dryer

### NO HEAT . I CHANGED THE HEATING ELEMENT,

Check to ensure you have 220v A/C to the dryer.
The dryer will run on 110v but will not heat.
Ck. the dryer cord where it connects to the dryer.
Some times one of the terminals on the cord may have burned up due to a bad connection.
Electric dryers are not sold with power cords since there are several different types of 220V outlets.

You may have a bad house fuse, Circuit breaker or 220V outlet.

Jan 16, 2010 | Dryers

### I have both washer n dryer that are 220v 4 prong each but theres only one 220v 4 prong wall outlet. do they make splitters for this ?

I would say no. I have never heard of a 220V washing machine, as a washing machine has no need for 220V. In any case though you would need to get the appropriate wire, cord and outlet and install a separate circuit for the washing machine.

Nov 02, 2009 | Bosch Nexxt WTMC 3300 Electric Dryer

### Generator plugs doesn't match cord

Hey steve. do you really need 240 volts for 120 v. circuits. the reason you have to have an adaptor plug is because on your 220 volt plug in , 2 of tthose prongs are hot and 1 is ground. for safety you need to get a plug adapter ( a regular 120 volt plug end ) run a ground from adapter to ground on 220 adapter. same with nuetral. you also need to ground your generator. there is usaully a ground lug on the bottom of the gen. Another way. if you dont really need 220 v. is to use both 120v. recepticals on gen. Run 2 chords to tranf. switch. and hard wire it in to switch. another way i did mine . when i lost power in this hurricane. i ran two # 10 chords from my 2 120v. recept on my gen to my breaker panel. when you do this you have to pull the service meter, if you dont when power comes back on it would backfeed through your gen.then i turn all my 220v. breakers i was able to run lights ,ciling fans, freezer, ice box,washing machine and gas dryer , tv's computors etc. . but to do this, you probably need someone that knows what they are doin.

Sep 18, 2008 | Coleman Powermate Premium Plus 6250W...

### The power is out because of Hurricane Gustav. I have a 6500 watt portable generator and would like to use our clothes dryer which has a 220 volt requirement. Is that possible, and is there a special...

Dryers require a 40A circuit breaker to handle the current. According to Ohms Law: Watts = Volts * Amps. Therefore, you require a power capacity of 220V * 40A in order to safely run the dryer, which is 8800 Watts. This means your generator does not have enough capacity to run the dryer. If we consider the full power of your generator at 6500 Watts, this only allows for 29.5A, which is not enough to run your dryer.

If it WAS possible, you would need to ensure that you ran a 30A heavy extension cord with the correct 220V plugs and receptacles on the end. This would require at least 10gauge 3-conductor wire, which is quite expensive.

However, that point is moot, since your generator does not have the capacity to run your dryer. You could try it, but I rather suspect that the dryer will trip the 30A breaker on the genset circuit. If you do try it, make sure you run a 10-gauge, 30A extension cord or you could have a fire.

Sep 06, 2008 | Dryers

### Hooking an electrical dryer to a breaker

You will typically need a 40 amp 220V circuit for this ( check with local building inspectors).  You will need to run some hefty wire probably #8 three wire  (again check) and install the type of plug receptacle that is on the  dryer cord.

Inside the breaker box you will need a dual breaker 220V breaker rated at 40 amps.  The wire coming into the breaker box will need to be clamped in place with appropriately sized wire cable clamp where the enter the box through a knockout- available at any hardware store.

Now the big question-  why are you switching to electrical?  Gas is pretty much half as expensive as electricy  and will dry the clothes faster (usually gas dryers generate more heat than electrical ones).   Just wondering..

Oct 20, 2007 | Dryers

### Electric Dryer

If your dryer came with a 4-prong plug, do not change it. For the very reasons you quoted with the article, you may screw up the 110v accessories required of your appliance (like the clock or digital display). It is best to change the household outlet to a 4-prong type. Just make sure your wiring is correct. You will need a neutral on the 4th leg, which means you will probably have to run new wiring from the outlet to the distribution panel.

Jun 09, 2007 | LG DLE2514 Electric Dryer

## Open Questions:

#### Related Topics:

157 people viewed this question

Level 3 Expert

Level 3 Expert