Question about Desa International ReddyHeater® R115DT Utility
There should be a reset button near the rear of it.when you turn it on,theres a fire eye that must see the flame within a few seconds,if it doesnt see the flame, it will kick the reset and kill the power so that youre not filling the burner with raw fuel and potentially making a nice little bomb. if you reset it and it continues to kick out, youll need to have it serviced.
Posted on Sep 27, 2009
Mske sure the rape switch is depressed and the heater is sitting upright on a solid surface. Good Luck _Ned_
Posted on Sep 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 21, 2015 | Bosch Water Heaters
Feb 02, 2015 | Heating & Cooling
Nov 18, 2011 | Goodman Heating & Cooling
Apr 30, 2011 | Philips 47PFL6704D LCD TV
Dec 21, 2010 | Reddy R70ET Utility Heater
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Dec 12, 2010 | Reddy Heater-30-55,000 BTU Variable
Oct 09, 2010 | Honeywell (CT62B1015) Baseboard Heater
Jul 16, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 13, 2007 | Honeywell HZ519 Baseboard Heater
103 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: