Question about Compaq 204015-001 - UPS T700 - UPS - 700 VA - UPS battery (204015001UPS) UPS System
Bypass not available is a common alarm.
This is because the input and ouput parameters
volts and frequency do not match, suggest checking these with meter or using ups sw and comp.
Bypass will not function if either v or f is incorrect, check manual for specs.
Post more info about batt on load with mains conected please, as this could mean major fault such as rectifier failure or micro malfunction
Hope this helps, thanks for asking FixYa
Posted on Sep 27, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 14, 2015 | Powerware 9390 UPS System
Feb 18, 2013 | Eaton Powerware 9355 UPS System
Pins 5 & 6 - Any-Mode Shutdown
1. Pin 6 of the 9-pin communication connector is used for "Any-Mode Shutdown"
of the UPS output. This control input may be used in special applications
to disable the UPS output power-both Inverter and Bypass.
2. The Options tab allows the behavior of the Any-Mode Shutdown feature to
be modified. When the program opens, or the REFRESH button is pressed,
the UPS setting is read by the configuration program and displayed.
Pin 6 Logic
If version 1.6 (or later) is used with an earlier Liebert GXT2U model (with an
earlier UPS firmware version), the Any-Mode Shutdown features cannot be
If the configuration program is used with an earlier UPS model (with an
earlier UPS firmware version) that does not support the modification of these
settings, the Options tab will display a reminder of the factory default
settings. These cannot be changed.
Note that when this option is selected and the UPS output is
disabled using Pin 6, the UPS output can turn on automatically
and without warning if the Pin 6 connection is changed.
DO NOT CHANGE THIS OPTION from the factory default
setting unless you are ready to install a normally-closed
connection between Pins 5 & 6. This connection must be
maintained to use the UPS or to use the configuration program
again, including the ability to change the UPS setting back to the
default setting using the configuration
Sep 05, 2011 | Liebert GXT2-10000R230 (GXT2-10000R230)...
Aug 23, 2011 | Eaton Powerware 9155 UPS UPS System
Nov 03, 2010 | APC Symmetra Tune-UPS technical support -...
Oct 14, 2009 | Eaton PW9390 UPS System
Oct 13, 2009 | Powerware 9125 UPS System
Jul 19, 2009 | APC Smart-UPS 1000VA UPS System
Feb 20, 2009 | APC Silcon UPS System
261 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: