Question about Reddy R70ET Utility Heater
Hi I have a Williams Wall gas heater that has a lit pilot but will not come on? Can You help me please?
If these are newer units 5 years or newer, there may be a thermal safety device up near the top. Follow the wires to find it. if you have this, bypass it by connecting the two wires going to it to each other and not the little disc. If this does not get the burner to ignite, then the next culprit or you do not have one then next is the pilot generator. This is the round cylinder next to the pilot flame. It and has 2 wires connecting to the gas valve. Remove it from the pilot assembly, it usually is just a clip, unscrew the 2 wires and pick up a new one. The connection on the gas valve has these wires labeled as TP for thermopile (dont ask, I don't know) replace in reverse as removed.
Posted on Dec 18, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2015 | Williams Heating & Cooling
Nov 01, 2015 | Williams Heating & Cooling
Nov 09, 2013 | Heating & Cooling
Feb 26, 2013 | Williams (5009622) Ceramic Gas Wall...
Nov 18, 2012 | Williams (5009622) Ceramic Gas Wall...
Nov 08, 2011 | Williams (5009622) Ceramic Gas Wall...
Feb 26, 2011 | Williams 3003622 Ceramic Wall Mounted...
Nov 11, 2010 | Williams 6508732 Gas Heater
Oct 18, 2010 | Williams (5009622) Ceramic Gas Wall...
Jan 01, 2010 | Williams Heating & Cooling
Jul 12, 2017 | Reddy R70ET Utility Heater
2,054 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: