Question about Heating & Cooling
No power will not let contactor pull in on outside unit - if capicitor is for fan and compressor and bad - neither will come on when contactor pulls in - low freon press. switch or if outside fan tripped unit on high pressure - could be manual reset - thermostat wires bad would not let run signal get to outside unit
Posted on Sep 24, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 11, 2010 | Goodman PHKJ048-1 Air Conditioner
Jul 17, 2010 | Heating & Cooling
Jul 15, 2010 | Heating & Cooling
Sep 19, 2009 | Goodman CKL36AR36 Air Conditioner
Jul 31, 2009 | Premier Heating & Cooling
Jun 16, 2009 | Goodman CLJ36AR42 Air Conditioner
May 02, 2009 | Heating & Cooling
Apr 27, 2009 | Carrier Heating & Cooling
Aug 19, 2008 | Weather King 10AJA6001AH Air Conditioner
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
Oct 22, 2017 | Heating & Cooling
154 people viewed this question
Usually answered in minutes!