Question about Fahrenheat Heating & Cooling
This is for my 1996 built home. It is a Fahrenheat Fan Forced Wall Heater FZL 4004 A and the plastic knob is stripped out and will not turn..just spins. This plastic knob is grey with long stem and says "Warmer" with arow going around. Can I get this item from you? Thanks S Thayer 863-324-5384 or firstname.lastname@example.org
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
A few companies sell child-proof covers that prevent little fingers and small objects from getting into the radiators. Try searching Child-safe baseboard heater covers in a google search or PexSupply.com.... we use them in daycare centers.
Posted on Jan 30, 2009
SOURCE: not sure hooked up correctly
You should have a licensed electrician connect this unit for you.
That being said you need to supply 240v to the unit. You will need a true two pole breaker. (not a split or a twin) There should be two screws or lugs and two slots or clamps on the bus side. These slots must span both phases of your panel. You can measure the voltage across the two screws if you are uncertain, it should read 240v.
Next connect a piece of 12/2 wire to the two screws. Use the black and the white. Land the bare copper wire on the ground bus in the panel.
Then at the unit, land the bare ground to the ground screw and connect your 12/2 to the wires in the unit. You may find the wire nutted together. This is normal, and allows "feeding" the unit from either side. If you are unsure measure the voltage here also, across the white and the black. It should be about 240v.
Posted on Feb 09, 2009
Tips for a great answer:
Feb 08, 2015 | Fahrenheat Heating & Cooling
Feb 14, 2011 | Fahrenheat (FFH1614) Wall Mounted Panel...
Jan 02, 2018 | Fahrenheat FUH5-4 Heater
Apr 23, 2010 | Fahrenheat (FFH1614) Wall Mounted Panel...
Oct 09, 2008 | Fahrenheat (FFH1614) Wall Mounted Panel...
Jan 05, 2008 | Fahrenheat FBE15002 Baseboard Heater
Dec 13, 2007 | Fahrenheat FFH1615 Heater
Dec 06, 2007 | Fahrenheat (FFH1614) Wall Mounted Panel...
157 people viewed this question
Usually answered in minutes!