Question about Cooper Industries Cooper Wiring 2158V 3 Gang 2 Toggle Switch- Duplex Wallplate, Ivory
I'm trying to wire a 3 gang box that has 15 amp power into it which consists of a single pole dimmer switch, a 3 way fan/light switch and a 3 way dimmer switch. I believe i'm to nut all the white together, ground together but not sure about the hot black whether I pigtail it to all the switches or what? a diagram would be fantastic!
WARNING: Do not attempt to do this work unless you completely understand the information provided below. If in doubt call an electrician.
Always make sure the power is disconnected from all possible sources before making any connections. Your description of the problem indicates that there may be multiple power wires coming into the same box. In that case local codes may require that the box be partitioned to prevent exposure to voltages up to 220 volts.
You need to determine where each wire goes to know how to connect them together. You cannot rely on color alone. If the power supply runs through the box to the loads then most (but probably not all) of the white wires will be connected together. If the power runs to the load boxes first then none of the white wires in the switch box should be connected together. They are used to run the switched/dimmed power back to the loads (and should be taped to cover the white in the box). In that case each switch has its own power input and they should not be tied together. A wire (could be black or white with black tape) brings power from the load box, gets connected to the input terminal of the switch and the corresponding black wire carries the switched power back to the load. The fan/light switch will have one power in and a switched power out for the fan and another for the light. The 3-way will have one "power" in (or it could be the final power out to the light) and two "carrier wires that connect to the other 3-way switch. If the power supply goes through the switch box then there will be at least 10 wires in that box. In that case see the attached diagram:
Posted on Sep 23, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 14, 2015 | Electrical Supplies
Sep 05, 2013 | Cooper Industries Cooper Wiring 2158V 3...
Feb 26, 2013 | Electrical Supplies
Feb 10, 2012 | Leviton MFG L00-IPI06-1LM DIMMER SLIDE...
Aug 19, 2011 | Leviton DECORA TWO GROUNDING SWITCHES...
Aug 16, 2011 | Cooper Industries Cooper Wiring 2158V 3...
May 28, 2011 | Cooper Industries Cooper Wiring 2158V 3...
May 21, 2011 | Leviton 15a 120v Sp Switch
Jan 14, 2011 | Lutron S-603PG Skylark Single Pole/3-Way...
10,396 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: