Question about GE AJCH10ACB Built-In Room Air Cool Unit
OIL WONT WORK IN THE PLACE OF LP OR VICE VERSA!
And correct You can addapt SOME burners to LP. Check with MFG to be sure. SOme Burners are dedicated to 1 fuel only IE LP only or NG only.
The LP has no regulator needed at the appliance it is regulated at the tank regulator, or on some 2 stage systems at the inlet to the building.
11" - 13" water column is the range for LP
If you cant find any MFG to answer your question take the name off the GAS valve you use and any model number on the gas valve and attempt to inquire form those numbers as to availability of lp change over. IF YOU DONT FIND ANY MFG OR INSTRUCTION MY ADVISE IS EITHER REPLACE THE VALVE WITH ONE THAT YOU KNOW IS APPROVED. A safety warning here is worth all the money because you cant save enough on the price of a new heater to replace any body and very few houses. Keep in mind that the spuds or orfices have to be changed also and some burners require reset of the Combustion Air inlet.
Posted on Mar 02, 2009
11" of water colum on Propane (roughly 1/2 pound). Oil runs on 100 PSI.
Posted on Dec 13, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 25, 2018 | Honeywell Heating & Cooling
Feb 26, 2015 | Cozy Heating & Cooling
Feb 25, 2015 | Garland Kitchen Ranges
Hello, Most newer gas furnaces (propane or natural gas) has one of several different types of igniters. The most common one is called a hot surface igniter. This is a ceramic easy to break, glow coil, glowing igniter. Some has a Spark igniter that lights all the burners from a constant spark and some light the burners off a pilot proven /spark igniter. This one sparks then lights a pilot then the burners will come on. In any case if any of these types are not working they could be cracked or broke. Also the inducer draft motor has to be running, the little motor that hooks to the exhaust of the furnace ( if it has one ). This causes the pressure switch to close then the igniter should come on. My suggestion is to call a qualified service tech from your area to assist you. To determine which one of these may be your problem they will have to perform several test. Hope you get going soon. I hope this helped. J
Jan 27, 2011 | Coleman Propane Forced Air Heater...
Nov 08, 2010 | Heating & Cooling
Jan 31, 2010 | Reddy Heater RLP100 Portable Forced Air...
Jan 04, 2010 | Coleman Propane Forced Air Heater...
Dec 07, 2008 | Honeywell Power Humidifier: Furnace...
Nov 06, 2008 | Heating & Cooling
Aug 06, 2008 | GE AJCH10ACB Built-In Room Air Cool Unit
144 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: