Question about Goodman GMS90703BXA Heater
The corresponding code says "open high limit". I havent timed it but the initial cycle seems like it lasts 20 minutes or more. Thanks for any help!!
The high limit is sensing the internal temprature of the furnace.If your filter is very dirty or you have to many of the registers/dampers shut it will cause the temp. of the furnace to exceed its rating and the high limit will open the circuit and shut down the flow of gas. Your blower will then run until the furnace has cooled and the switch will close and allow it to come back on. This is bad for your furnace, make sure your filter is clean and you dont have to many registers shut. If you have run the unit without a filter the problem could be much more sever requiring blower wheel and coil cleaning and possibly a cracked heat exchanger.
Posted on Sep 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 21, 2015 | Heating & Cooling
Jan 24, 2008 | Goodman GMS90703BXA Heater
Apr 08, 2015 | Mitsubishi WD-65731 65-Inch 1080p DLP HDTV
Jan 21, 2015 | Sony BRAVIA Televison & Video
Nov 10, 2011 | Heating & Cooling
Mar 08, 2011 | Sony KP-57WS500 57" Rear Projection...
Dec 03, 2010 | Goodman GMS80903BNA Heater
Jun 25, 2017 | Heating & Cooling
Jan 04, 2010 | Televison & Video
Aug 01, 2009 | Bosch SHU5315UC Dishwasher
250 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: