Question about Goodman CKL36AR36 Air Conditioner
That seems like too long at most delays and lock outs that are built into a system throught the tstat and the outdoor systems defrost board should only take about ten minutes. at most twenty if you had a dual fuel system. (heat pump outside and gas furnace inside). check the installer programming on your tstat may have a compressor lock out set too long for some reason.that or possible bad lowvoltage connections or maybe ants in you contacts at compressor outside. could be many things
Posted on Sep 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 15, 2014 | Goldstar Heating & Cooling
Sep 01, 2010 | Heating & Cooling
Jul 18, 2010 | LG LWHD2500ER Wall/Window Air Conditioner
May 04, 2010 | 2005 Pontiac Grand Am
Nov 26, 2009 | Refrigerators
Jun 17, 2009 | Carrier 38BRC036 Air Conditioner
Jun 13, 2009 | Ingersoll Rand Type 30 Reciprocating Air...
Jan 12, 2009 | Magic Chef CTB1922 Top Freezer...
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: