Question about APC Matrix-UPS 5000 UPS System
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: APC UPS no power
The unit might have a dead battery, blow fuse, or a bad board.
Your best bet is to talk to an APC rep. Worst case, APC has a trade in program, and can give you a discount on a new one.
Try Chatting with an APC Support agent online.
Here is their direct link:
Chat with a Support Agent
Chat with Support for immediate assistance with your APC Back-UPS, Cable, Surge Protection, Notebook and Mobile Device accessories and products. Agents are available Monday through Friday from 8:00 a.m. to 8:00 p.m.
Posted on Feb 07, 2008
SOURCE: Overload light in APC RS 800 UPS
it seems that the inverter circuit of your UPS is dying. the solution here is you have to open up the UPS and check the inverter circuit. to make easier, check the power mosfet if its leaking.
Posted on Aug 14, 2009
On this unit, the likely culprit is the battery and that it needs to be replaced.
With that, you may want to think about the pros and cons of replacement versus buying an entirely new unit.
This unit is a relatively low end ups and the surge supression uses MOVs that wear out with repeated absorption of energetic spikes. That's why the better (and higher cost) UPSs and surge suppressors don't use them. They're not really that good anyway due to their relatively high transient impedance. The better equipment uses a "transorb" -- basically a back-to-back high voltage zener diode optimized for low breakover impedance and high instantaneous power capability. Unless the transient exceeds the design parameters of the circuit, these do not wear out and do not degrade. That being said, I will assume that you would likely replace this unit with a similar one.
The flashing may not be the battery at all and may be the charging circuitry, thus your new battery may not live very long (half the life that you would expect.
Many batteries out there are refurbs and have issues as all used parts do.
If you contact APC, they will likely give you a 35% discount on purchasing a new product.
The difference in price in the battery replacement vs. ups replacement at this level may only be a few dollars more.
I promise that I am not a UPS salesman, I just deal with many on a daily basis; therefore I am giving my two cents to try to thelp you avoid problems a year from now.
Posted on Dec 30, 2009
Testimonial: "Outstanding answer with right amount of detail. I swapped battery with identical APC UPS that I have and vfd that battery was cause of warning tone."
Tips for a great answer:
Jul 29, 2014 | APC Matrix-UPS 5000 UPS System
Nov 23, 2011 | APC Matrix-UPS 5000 UPS System
May 05, 2011 | MGE UPS Pulsar Evolution 500 UPS System
Feb 28, 2011 | APC Smart-UPS XL 5000 RM (SU5000R5XLTXFMR)...
Mar 16, 2010 | APC Matrix-UPS 5000 UPS System
Dec 27, 2009 | APC Matrix-UPS 5000 UPS System
Jun 23, 2009 | APC Matrix-UPS 5000 UPS System
Mar 17, 2009 | APC Smart-UPS 700VA UPS System
Apr 25, 2013 | APC Matrix-UPS 5000 UPS System
106 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: