Question about Generac 100 Amp 120/240-Volt Transfer Switch #RTSN100A3
After installation, followed installation guide's instructions for manual test. Utility power off. Breakers on Generac panel off. Generator's breaker off. Generator's mode switch set to off. Manually operated transfer switch to down position. Switched generator's mode switch to Manual start ... readout ''cranking, attempt 1'' for a few seconds ... but no cranking whatsoever, whole unit is silent ... then ''RPM Sense Loss'' message.
Verified natural gas pressure is present. Battery's brand new and shows full charge. 12 volts present at lug under red cap by starter. Fuse is good.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 20, 2015 | Generac Power Systems Centurion by 16000...
Oct 15, 2014 | Generac Guardian 8kw Standby Generator
Dec 01, 2013 | Generac Electrical Supplies
Aug 10, 2013 | Generac Guardian Guardian 28" Battery...
Aug 11, 2010 | Generac Guardian Series 5502 10 kW...
Mar 22, 2010 | Generac Guardian 100 Amp Transfer Switch...
Jan 22, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Jul 01, 2009 | Generac Guardian 200 Amp Transfer Switch...
Apr 12, 2009 | Guardian Electrical Supplies
Apr 06, 2009 | Guardian Electrical Supplies
3,115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: