Question about Generac Guardian 100 Amp Transfer Switch NEMA 3R
Generator came on after a recent power outage, but there was no power in the house.Same generator as the original post (runs on propane). Also had 2nd battery explode, and replaced 2 weeks ago. How can I determine if this is a transfer switch problem? a
At the point the transfer switchis suppose to transfer put a dc volt meter across terminals 23 and 194 in the transfer if you do not show 12VDC. Then you have a relay hanging upon the PCB board in the generator, need to replace board. If you are showing 12VDC and the switch is not transferring the problem is in the switch itself.
Posted on Nov 22, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2014 | Electrical Supplies
Oct 16, 2014 | Generac 10kw Whole House Generator with...
Aug 20, 2014 | Electrical Supplies
Dec 02, 2013 | Kohler Residential Standby Generator-14 Kw...
Jul 27, 2011 | Dayton Heating & Cooling
Feb 26, 2010 | Briggs & Stratton Power Products 5,550...
Sep 04, 2009 | Generac Guardian 100 Amp Transfer Switch...
Jul 20, 2009 | Dometic Rooftop RV Air Conditioner
Feb 18, 2009 | Coleman Powermate Powermate 5000W...
239 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: