Question about Cooper Industries Cooper Wiring CS220V AC Quiet Switch, Double Pole, Ivory
How to wire a cooper cs220v double pole switc. The drawing on the box doesn't match the part exactly. It shows the load placed between 2 black screws and the line connected to 2 white screws.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
WARNING: Do not attempt to do this work unless you completely understand the information provided below. If in doubt call an electrician.
Always make sure the power is disconnected from all possible sources before making any connections. Your description of the problem indicates that there may be multiple power wires coming into the same box. In that case local codes may require that the box be partitioned to prevent exposure to voltages up to 220 volts.
You need to determine where each wire goes to know how to connect them together. You cannot rely on color alone. If the power supply runs through the box to the loads then most (but probably not all) of the white wires will be connected together. If the power runs to the load boxes first then none of the white wires in the switch box should be connected together. They are used to run the switched/dimmed power back to the loads (and should be taped to cover the white in the box). In that case each switch has its own power input and they should not be tied together. A wire (could be black or white with black tape) brings power from the load box, gets connected to the input terminal of the switch and the corresponding black wire carries the switched power back to the load. The fan/light switch will have one power in and a switched power out for the fan and another for the light. The 3-way will have one "power" in (or it could be the final power out to the light) and two "carrier wires that connect to the other 3-way switch. If the power supply goes through the switch box then there will be at least 10 wires in that box. In that case see the attached diagram:
Posted on Sep 23, 2009
Take the black going to the light off the center and hook where the white going to the light is now....then hook the white to the light with the other white and you will be good to go...You almost had it right...
just a couple of adjustments....:-)
Posted on Oct 11, 2010
bare ground goes to green screw
dark screw goes to hot from breaker
silver screw to neutral
brass screw goes to load (light)
Add a comment any time
You are replacing single pole light switch?
Single pole switch has 3 wires: black and red and bare copper
New device has 4 different colored screws: green, dark, brass, silver
Bare copper goes to green screw.
Black wire goes to dark screw
Red wire to brass screw
Nothing on silver screw for a moment. Test circuit and make sure light turns on-off.
If lights works, then good so far.
Now let look at silver screw. Neutral wire has to connect to silver screw.
In back of your electrical box are white wires twisted together and covered with wire nut.
These are neutral wires.
You must connect another short piece of insulated wire to these neutral wires and run that wire to silver screw.
The neutral wire will complete circuit to receptacle.
If you do not have neutral wire, then receptacle will not work in that box without additional wiring.
Hook up neutral wire to silver screw.
Now turn on power and click switch again.
If circuit breaker trips, then reverse your red and black wires.
Otherwise this should be correct wiring.
Posted on Dec 08, 2010
Ok you have GFCI combination switch-plug.
Wires coming out of back of device are connected to "Load" wires.
Load are the black and white wires that go to fan, light, motor.
The black and white wires coming from circuit breaker connect to terminals marked "Line"
Look at back of device for markings.
Black wire from breaker goes to brass screw, white wire goes to silver screw.
There is one more set of screws on device. Device usually arrives with tape over these two screws.
This is what those screws are for: If you are working in a junction box, then three cables enter box.
One cable is for Line wires from breaker box.
Second cable goes to Load (light-fan-motor) that is controlled by switch.
Third cable goes forward to another switch or outlet >> and those wires connect to last set of screws on combo device. Black to brass and white to silver.
Add a comment for more free help.
Also take advantage of fixya expert assistance live.
For a price, expert works with you via e-mail while you work on circuit or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on Feb 17, 2011
Tips for a great answer:
Aug 17, 2014 | Cooper Wiring Devices 274V-BOX DECORATOR...
Dec 01, 2013 | Cooper Wiring Devices Electrical Supplies
Dec 18, 2012 | Electrical Supplies
Sep 02, 2011 | Cooper Industries Cooper Wiring CS220W AC...
Aug 16, 2011 | Cooper Industries Cooper Wiring 2158V 3...
May 28, 2011 | Cooper Industries Cooper Wiring 2158V 3...
Feb 14, 2011 | Leviton COMBINATION SINGLE POLE TOGGLE...
Dec 03, 2010 | Cooper Wiring Devices 277W-BOX SINGLE POLE...
Jan 28, 2010 | Cooper Wiring Devices Motion Sensing...
Sep 19, 2008 | Cooper Industries Cooper Wiring CS220V AC...
302 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: