Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Need to have more numbers in model number to be sure There's about 30 T841 t'stats and some are1, 2, and 3 stage heat pump and some 1, 2, and 3stage AC.
If you have
R to transformer
G to fan relay
Y to contactor in outdoor unit
W to Gas valve
You have the thermostat wired right.
Depending on the T'stat B could be the common side of the transformer or 2nd stage heat.
W2 terminal are for 2nd stage heat
You need to put the thermostat on cool and lower the setting to bring on the cooling. Then go outside and see if you have power to the outdoor unit and 24 volts to the contactor coil.
Posted on Sep 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 14, 2016 | Heating & Cooling
Sep 11, 2015 | Honeywell CT31A - Economy Heat/Cool...
Dec 19, 2010 | Honeywell Heating & Cooling
Nov 30, 2010 | Honeywell Heating & Cooling
May 28, 2010 | Honeywell Programmable Thermostat Heater
May 02, 2010 | Heating & Cooling
Mar 16, 2010 | Dometic Rooftop RV Air Conditioner
May 24, 2009 | Heating & Cooling
Feb 07, 2009 | Haier Energy Star ESA3183 Air Conditioner
Sep 04, 2008 | Honeywell Heating & Cooling
215 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: