Question about Fahrenheat Electric Convector Baseboard Heater, 240 Volt
Can't find instructions
I have the solution, finally after looking for 2 days.
First off, I couldn't quite put it all together based on what I was reading. I finally tracked down the Fahrenheat web site (www.fahrenheatpro.com). And called tech support (800) 452-4179.
To wire 2 BB units to 1 tstat.
1. Use #14 wire for 0-12 amps, #12 wire for 12.1 to 16 amps and #10 wire for 16.1 to 24 amps.
2. I have a 12/2 wire going from the tstat to BB#1 and another 12/2 wire going from BB1 to BB2.
3. Onthe left side of the heater, you will have 2 sets of black wires tied together with a nut (on right side it's 2 sets of Black/Red wires). You can use either side of the heater. For the purpose of explaining this, lets use the left side, 2 sets of black wires.
4. Undo one of the sets of black wires (it doesn't matter witch), the other set will be left alone.
5. Take the black wire coming from the tstat and tie it into one of the black wires from the heater and the black wire going to the second BB unit. So you will have those 3 wires tied together with a nut at the 1st BB unit.
6. Take the white wire coming from the tstat and tie it into the other black wire from the heater and the white wire going to the other BB heater. Again, you will have 3 wire tied together here.
7. At the second BB unit, tie the black wire coming from the 1st unit to one of the black wires in one of those 2 sets of black wires. Again, only undo 1 set of wires at the 2nd unit, leave the other one alone. Tie the white wire coming from the 1st unit to the other black wire.
8. Make sure ground wire in grounded at the tstat and at both BB units.
Hope this helps...... If I was less clear than I hoped, call tech support and they will walk you thru it....
Posted on Oct 16, 2008
How do you wire a plf 2004 heater using a remote thermostat?
Posted on Jan 05, 2008
240 volt wall mount baseboard heater. at either end of the heater is a service plate. it may also have an integral thermostat on one end. feed your line into the side with the thermostat. the thermostat has two wires a black and a red, with similar wire colors going to the element. wire your line on one red and one black on the same side of the "stat." the not connected to anything side of the "stat." the rest of the heater is series wired to the overload and element. (factory wired) no need to touch anything here.
Posted on Dec 09, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 13, 2018 | Water Water Heaters
Oct 28, 2015 | Fahrenheat Electric Hydronic Baseboard...
Dec 15, 2012 | Bosch AE-9.5 Electric PowerStar PowerStar...
Aug 24, 2012 | Electronic Arts Pet Society
Sep 04, 2011 | Fahrenheat Electric Hydronic Baseboard...
Jan 11, 2011 | Fahrenheat Electric Convector Baseboard...
Nov 30, 2010 | AOpen i945Ga-PLF (918EA10I40) Motherboard
Oct 26, 2010 | Fahrenheat Electric Hydronic Baseboard...
Jan 06, 2010 | Fahrenheat Electric Hydronic Baseboard...
Oct 17, 2009 | Heating & Cooling
1,595 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: