Question about Heating & Cooling
Have a York less then 3 years old unit, the fan stopped spinning, and hummed. Took out the capasitor and cleaned the terminals - put it back in and the fan spun back wards - I suspect the capacitor is not functioning properly, and that the fan motor sustained damage.....I also inspected the fan motor unit, and the shaft spins freely......at this point I am ready to replace them both. Now the next question - I have found the motor and capasitor on several sites that support HVAC - what I found was capasitors for 18$ verses the 118$ i am being qouted at stores and most web sites....what's the difference?
Your capacitor is definitely the culprit here.
It should be a dual capacitor. Meaning it has 3 terminals on one capacitor. "C" "H" and "F" would be the markings for power in,"C" out to fan "F" and out to compressor "H".
It also has a mfd(microfarad) value on the capacitor as well as a VAC rating of 370 or 440 volts ac. A 440 VAC can be used in place of a 370vac.
The other specs may be something like 40/5 or 35/5 or 40/7.5 etc.
The capacitor replacement should be exact as far as the microfarad rating is concerned.( eg. 40+5).
The money requested through various sites is just that....various. These dual caps may sell around 30-50 dollars for a quality capacitor. If you wish to spend the $118 I will sell you all as many as you would like.
Posted on Sep 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 03, 2017 | AC Cars & Trucks
Apr 14, 2013 | Carrier Payne 2.5 Ton Air Conditioner...
Apr 23, 2017 | Heating & Cooling
Aug 21, 2011 | Heating & Cooling
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Dec 10, 2010 | Heating & Cooling
Jul 19, 2009 | Heating & Cooling
May 28, 2009 | Maytag 22 cu. ft. Bottom Freezer...
288 people viewed this question
Usually answered in minutes!