Question about Pentair Minimax NT Heater
Minimax NT heater is knocking. Could it be gas pressure? Is there an inlet filter I can check to see if clogged?
More often than not this will be the by-pass and thermal regulator. Both of these are inside the water manifold on the side of the heater. I will usually replace both if one is bad. If one is bad the other can become damaged and the labor and parts to do this are a big part of the job. Also check and see if you have a by-pass on the plumbing going to the heater. This will be a valve bridging the water in to and out of the heater. If you have one it should be 80-90% closed so it forces water through heater. If any of these are bad it will let water go past the heater and the water inside the unit will overheat and turn to steam and with no place to go it just expands and starts banging.
Posted on May 17, 2010
Assembly valve need to be replace
Posted on Sep 13, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 05, 2016 | Pentair Minimax NT Heater
Jul 26, 2014 | Pentair Minimax NT Heater
Aug 03, 2013 | Pentair Minimax NT Heater
Mar 22, 2012 | Pentair Minimax NT Heater
May 30, 2011 | Pentair Minimax NT Heater
Mar 14, 2010 | Pentair Minimax NT Heater
Jun 22, 2009 | Pentair MINIMAX NT TSI IGNITER
Jun 08, 2009 | Pentair Minimax NT Heater
Jan 22, 2018 | Pool & Spa
133 people viewed this question
Usually answered in minutes!