Question about Heating & Cooling
Check the breakers,if they are not tripped then you have a problem with either the t-stat or the low voltage transformer in the furnace may be bad.To check for low voltage remove the front cover of the air handler and using a volt meter check for voltage between the red and common wire.
Posted on Sep 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 08, 2014 | Heating & Cooling
Aug 06, 2014 | Heating & Cooling
Aug 22, 2013 | Intertherm Heating & Cooling
Aug 21, 2013 | Heating & Cooling
Jul 31, 2012 | Goodman Heating & Cooling
May 14, 2011 | Carrier Air Tools & Compressors
Sep 04, 2009 | Carrier 38CKC030 Air Conditioner
Jun 15, 2009 | Heating & Cooling
Oct 22, 2017 | Heating & Cooling
62 people viewed this question
Usually answered in minutes!