Question about Heating & Cooling
Fan runs but the heat will cycle once and then stop, checked and replaced the ignitor and servised the unit, what's up
Figured it out, the problem was return air ducting was capped off, by the construction crew, thanks
Posted on Dec 07, 2007
A model number may help. Also, are you refering to the inducer fan?
If so, jump out the pressure switch. If it runs, start looking for a blockage in the combustion chamber, blockage in the line to the pressure switch, a bad inducer fan (not getting enough pressure to close switch) or a bad pressure switch.
Posted on Dec 06, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 31, 2015 | Carrier WEATHERMAKER 48TCEA 4.0 ton Gas...
May 23, 2017 | Dometic Rooftop RV Air Conditioner
Jun 06, 2012 | Dometic Rooftop RV Air Conditioner
Mar 25, 2017 | Heating & Cooling
Sep 23, 2011 | Carrier 50TJ028 Rooftop Electric Cool Air...
Oct 30, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 10, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 05, 2008 | Dometic Rooftop RV Air Conditioner
612 people viewed this question
Usually answered in minutes!