Our aprilaire humidifier is only 4 years old and it does not seem to be working. We have static in the house and when I did test mode it never drained water like it was supposed to. Any ideas what I can do...
Hope this helps, check and see if humidistat is set to 35% humidity and that bypass damper on humidifier is in the open position or winter position.(humidistat is usually located on cold air return duct near furnace). Next, replace humidifier media pad, remember to replace media pad (filter) annually, you also may want to clean any lime deposit out of humidifier housing with a solution of warm water and white vinegar before installing your new media filter.Remember to turn power off at side of furnace when cleaning humidifier and replacing media. Before installing new media turn power back on to furnace, set humidistat to the on position, turn furnace thermostat above room temp., and inspect humidifier to see if water is running from top,(you may want to have a bucket under humidifier when checking for water), if you see water running, turn power back off to furnace, properly install new media filter, reconnect humidifier cover & set humidistat to 35%. If you do not see water present, check water supply valve to humidifier and make sure its turned on. If water supply valve is open, then check water supply tubing for blockage.And the last things to check is to make sure all registers through out your home are open and not blocked by any objects, also make sure furnace filter is cleaned, if none of this works refer to installation manual to see if humidifier was sized and installed properly, Good luck.
Mar 03, 2010 |
Aprilaire 600 Humidifier