Question about Honeywell HE360A1027 Whole House Humidifier Humidifier
My humidifier is 2yrs old. When I turned it on this year I noticed that there is no water flowing through the pad area. Actually I took off the rubber hose that leads out of the little cylinder where the main water connection goes and there is no water flowing from there either. The humidifier turns on, I can hear the fan but there is no water flow. Any ideas out there as to why??? I tried the honeywell website but the had no information.
I has same problem and was able to fix ti by taking off the selonoid (cylinder) and then removing both fittings (where the water line enters and then exits the selonoid. The fitting where the water enters has a small pinhole that I found clogged and just cleaned it with a toothpick. After cleaning and reattaching everything, it works fine.
If that doesn't work, you might need a new selonoid which are around $70-$80.
Posted on Dec 08, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 31, 2013 | Aprilaire 400 Humidifier
Jan 23, 2011 | Honeywell HE220A1019 Whole House...
Jan 15, 2011 | Desert Spring DS3200 Humidifier
Mar 01, 2010 | Carrier LBP Humidifier
Feb 16, 2010 | Humidifiers
Oct 24, 2009 | Honeywell Power Humidifier: Furnace...
Oct 03, 2009 | Aprilaire 700 Humidifier
Apr 09, 2009 | Aprilaire 700 Humidifier
Jan 25, 2009 | Honeywell HE220A1019 Whole House...
Nov 30, 2007 | Honeywell HE360A1027 Whole House...
Jul 11, 2017 | Honeywell HE360A1027 Whole House...
Jan 09, 2014 | Honeywell HE360A1027 Whole House...
591 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: