Question about Rinnai Desa Vent-Free Infrared Gas Heater: Vent-Free Infrared Gas Heater(18,000 BTU)
How do i get the pilot to light
Is this a new heater or have you had it awhile? If new, yuo may have air in the line that will need to be bled out. The heater has a gas valve with a pilot setting on it. Make sure the gas is turned on. Turn the knob to the pilot setting and depress the handle. Holding it down and at the same time, press down on the red button that sparks. You may have to repeat this a few times. Once the pilot lights, continue to hold down on the pilot knob for about 30 seconds. When uou release the knob, the flame should stay o. If it does not, replace the thermocouple. Once the pilot flame is steady, turn the gas valve knob to on.
Posted on Nov 30, 2007
make sure you have the gas valve knob on turned to pilot while pressing that down while pushing the spark it should light or it is tripped on a safety like rollout switch or oxygen depletion sensor if equipped which all ventless heaters are
Posted on May 12, 2009
sounds like either a bad thermocouple or more likely a pressure regulator problem. should have unit checked by someone familiar with propane systems.
Posted on Jan 22, 2010
try this site. I don't know what numbers will work but they have parts for dyna glo.
Posted on Dec 09, 2007
Clean the pilot and if that does not help replace the thermocouple. Also make sure you have correct ventilation to the room as that can also cause this type of heater to shut down.
Posted on Nov 18, 2008
Tips for a great answer:
Nov 12, 2012 | Desa International Blower Glow Warm Wall...
Mar 13, 2010 | Dyna-Glo D-E37 Wall Mounted Panel Heater
Jan 10, 2010 | Desa International Blower Glow Warm Wall...
Dec 06, 2009 | Desa International Blower Glow Warm Wall...
Nov 03, 2008 | Desa International Blower Glow Warm Wall...
Jan 25, 2008 | Desa International Blower Glow Warm Wall...
Nov 19, 2007 | Rinnai Desa Vent-Free Infrared Gas Heater:...
1,492 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: