Question about Heating & Cooling
I have a intertherm heatpump that has the heat strips located in the outside unit. The heat pump works ok until the temp gets around freezing then not enough heat to hold the thermostat setting. I suspect the strips should be helping the heat pump but is not. I can manually turn on the emergency heat and get hot air. also there is a cycle when the heat pump blows ice cold air for about 2 minutes while in the heat mode. Hope yoy have some advice. Thanks
FIRST YOUR OUTSIDE UNIT PROVIDES HEAT BY USING A REVERSING VALVE TO CHANGE THE REFRIGERANT FLOW.THERE IS NO HEAT STRIPS OUTSIDE SECOND YOUR EMERGENCY HEAT TURNS ON ELECTRIC ELEMENTS INSIDE YOUR AIRHANDLER UNIT.IT SOUNDS LIKE SOMEONE HAS WIRED YOUR UNIT WRONG OR HAS THE THERMOSTAT SET IMPROPERLY.WHEN THE HEAT PUMP CANNOT SATTISFY THE SETPOINT THE THERMOSTAT IS SUPPOSED TO TURN ON YOUR ELEC. HEAT UNTILL THE LOAD HAS BEEN REACHED AND THE HEAT PUMP CAN CONTINUE TO MAINTAIN IT.
Posted on Nov 29, 2007
I have a Intertherm heart pump that the compressior is good on except the cinnection to it keeps shorrting out If you have an idea on repairing, SU
Posted on Oct 20, 2008
It sounds like you have a packaged unit for modular or manufactured housing. If this is the case I have noticed that they have a outdoor thermostat wired in series that does not allow the heat strips to come on unless it is satisfied at around 55 degrees. Remember this is inside the unit so it could be much colder outside. If this is not the case you may have a defrost problem, either in the defrost board or defrost sensor.
Posted on Dec 01, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 29, 2017 | Intertherm Heating & Cooling
Feb 03, 2017 | Honeywell Heating & Cooling
Feb 13, 2014 | Intertherm Heating & Cooling
Mar 01, 2017 | Haier Energy Star ESA3183 Air Conditioner
Sep 30, 2010 | Intertherm P3RA-060K Air Conditioner
Feb 23, 2010 | Dometic Rooftop RV Air Conditioner
Jan 31, 2010 | Heating & Cooling
Dec 06, 2009 | Ruud UAMB042 Air Conditioner
Jan 23, 2009 | GE Zoneline AZ55H09D Air Conditioner
Jun 18, 2008 | Intertherm Heating & Cooling
2,222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: