Question about Carrier Humidifiers
Model is Humcclfp1218A. I checked that there is continuity from the humidistat after turning it to the point where it clicks. I also read 24 volts from the leads attached to the furnace and there is 120v AC supplied to the fan of the humidifier. When the furnace starts up, the humidifier fan does not run and water is also not supplied to the element. Could the problem be the circuit board inside the fan assembly?
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Installation problem
I WOULD CHECK TO SEE IF YOU HAVE ENOUGH V/A OUT-PUT ON TRANSFORMER. I DONT KNOW IF YOURS CAME WITH ITS OWN TRANSFORMER. IF IT DIDNT YOU SHOULD HAVE A MINIMUM OF A 40 V/A RATING STAMPED OR PRINTED ON THE EXISTING TRANSFORMER. IF THE TRANSFORMER IS EXTREAMLY HOT ... YOU MAY NEED A 75 V/A TRANSFORMER WITH THE SAME VOLTAGES. INCREASING THE V/A CANNOT DAMMAGE ANYTHING IT JUST GIVES YOU MORE POWER WHEN EXCESIVE CONTROLS AND WIRING ARE ADDED TO A HVAC LOW-VOLAGE (24v) CIRCUIT. IF YOU LIKE YOU CAN CALL ME AT 727-363-7071. I AM A RETIRED HVAC&R CONTRACTOR WITH 45 YEARS EXPERIENCE. I HATE THE NEW SENSORS THEY HAVE TO ACTIVATE THESE NEW HUMIDIFIERS. I USE TO WIRE THE HUMIDIFIER TRANSFORMER (SUPPLIED WITH HUMIDIFIER) TO THE LINE (110V) SIDE TO THE LOW SPEED ON YOUR BLOWER MOTOR. THAT WAY THE ONLY THING THAT INTERUPTS THE CICUIT IS THE HUMIDISTAT. YOU NEVER WANT THE HUMIDIFIER TO RUN IF YOUR SYSTEM IS NOT "CALLING FOR HEAT". NEVER TRY TO ENERGIZE THE WATER SOLENOID THROUGH YOUR HEAT WIRE(USUALLY SMALL THE WHITE WIRE) FROM THE THERMOSTAT. THIS WILL RESULT IN BURNING YOUR HEAT ANTICIPATOR OUT ON THE T-STAT.
Posted on Apr 28, 2007
SOURCE: wiring problem
Sounds like you may have put 120v through a 24v solenoid and humidistat.
Is the HUM terminal on the furnace 120v or 24v?
If it is a 120v terminal you will need a 120x24v transformer and a new solenoid and maybe a new humidistat.
Posted on Jan 02, 2009
Some sump pump have a safty switch that will not let the hum. come on if the tank is full of water, I,m not sure if this is the type that you have but make sure that the pump is pumping water. Also your humidistat have an internal switch that it should be set to bypass not to power Note: some humidifier have their own power supply the 550 dose not
Posted on Feb 09, 2009
hook up the new transformer to the white (common) from the blower motor, and the lead from the blower motor hooked up to the heat term on the board. (just cut the wires and wire nut all three together)
Posted on Nov 18, 2009
SOURCE: Honeywell HE260 leaks somewhere
Neither, even if the solenoid or humidistat stick, it should always drain properly. Is the unit mounted on the cold air return duct or the supply plenum? If it's mounted on the supply plenum, the water panel might be getting blown forward and spilling the water. High efficient furnaces also can leak water on the floor if its drain is restricted. If hum. is mounted on return duct make sure drain is clear by blowing through it. On Honeywell hum's I've seen the rubber hose from the solenoid valve to the distributor tray leak too, check the rubber 1/4" hose.
Posted on Jan 21, 2010
Tips for a great answer:
Oct 09, 2013 | Aprilaire 700 Humidifier
Jan 22, 2013 | Humidifiers
Jan 03, 2013 | Carrier SBP Humidifier
Dec 04, 2012 | Aprilaire 700 Humidifier
Jan 21, 2012 | Carrier LBP Humidifier
Jan 19, 2011 | Carrier SBP Humidifier
Mar 03, 2010 | Aprilaire 600 Humidifier
Oct 12, 2009 | Honeywell HE220A1019 Whole House...
Nov 22, 2008 | Carrier SBP Humidifier
Dec 21, 2007 | Humidifiers
Nov 30, 2013 | Carrier Humidifiers
Jan 26, 2013 | Carrier LFP Humidifier
203 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: