Question about Heating & Cooling
Fan no coming on and hot air blowing
Shut the power off to the unit, spin the fan blade to see if it spins freely. If it doesn't spin freely, (there appears to be a little drag when you spin it),the bearings are bad, if it does spin freely, then try moving the motor shaft from side to side if there’s any play in the shaft side to side then the bearings are worn and motor needs replaced. Then, check the capacitor, if it’s bulging even slightly, the capacitor is bad and needs replaced. Most of the time people replace the capacitor if motor seems ok. If capacitor is ok, turn power on to see if the motor is getting the proper voltage, if it is and not trying to run, then the windings are probably open, the motor's bad and needs replaced.
The fan motor could have been your problem all the time, because if the fan doesn't come on or runs slow, it causes high head pressure,
which causes high amps, which could trip your breakers.
Posted on Aug 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 21, 2015 | Dryers
May 14, 2015 | Coleman Heating & Cooling
Jul 27, 2010 | Ruud Central System Air Conditioner
Jul 09, 2010 | Hitachi EC89 4 Gallon Twin Stack Air...
Jun 12, 2010 | Ruud UAKA018 Air Conditioner
Jun 06, 2010 | Dometic Rooftop RV Air Conditioner
Jul 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 29, 2009 | Dometic Rooftop RV Air Conditioner
Aug 21, 2017 | Heating & Cooling
111 people viewed this question
Usually answered in minutes!