Question about Goodman CLQ36AR49 Air Conditioner
My unit works perfect during cooling but I can not get it to heat, I changed the thermostat and the same results, it blows cool only.
Goodman energizes it reversing valve in the cooling mode. Usually in the "o" circuit of the thermostat wiring.You may have that wired hot somehow.
Posted on Nov 28, 2007
I just had a new unit installed and I am surfing for troubleshooting tips too. My unit is doing the same... cools well heat sucks. my problem has been isolated down to the reversing valve... It is constantly energised which means it is constantly in a/c mode even when kicking on the heat strips... We disconnected a line at the thermostat and it is working well as a heater now. You may want to check yours to see if it is actually kicking over into to heat mode... -rob
Posted on Nov 26, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 25, 2017 | Goodman Heating & Cooling
Jun 02, 2016 | Heating & Cooling
Oct 28, 2012 | Honeywell Programmable Thermostat Heater
Jul 28, 2010 | Heating & Cooling
Jul 12, 2010 | Goodman CLQ36AR49 Air Conditioner
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Mar 05, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 31, 2009 | Heating & Cooling
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Nov 10, 2008 | Goodman PHKJ048-1 Air Conditioner
570 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: