Question about Goodman CLQ36AR49 Air Conditioner
My unit works perfect during cooling but I can not get it to heat, I changed the thermostat and the same results, it blows cool only.
Goodman energizes it reversing valve in the cooling mode. Usually in the "o" circuit of the thermostat wiring.You may have that wired hot somehow.
Posted on Nov 28, 2007
I just had a new unit installed and I am surfing for troubleshooting tips too. My unit is doing the same... cools well heat sucks. my problem has been isolated down to the reversing valve... It is constantly energised which means it is constantly in a/c mode even when kicking on the heat strips... We disconnected a line at the thermostat and it is working well as a heater now. You may want to check yours to see if it is actually kicking over into to heat mode... -rob
Posted on Nov 26, 2007
Tips for a great answer:
Jun 02, 2016 | Air Conditioners
Nov 05, 2010 | Goodman PHKJ048-1 Air Conditioner
Jul 12, 2010 | Goodman CLQ36AR49 Air Conditioner
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
May 17, 2010 | Goodman CKL24AR24 Air Conditioner
Mar 05, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 31, 2009 | Air Conditioners
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Nov 10, 2008 | Goodman PHKJ048-1 Air Conditioner
Nov 25, 2007 | Air Conditioners
467 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: