Question about Honeywell CT3600 7 Day Electronic Programmable Thermostat Heater
I have a Florida Geo heat pump 2 stage with no aux.heat. It is controlled by a Zone Perfect Two-Zone Unit hooked up to two Totaline P274-0300-C thermostats. Everything works great this way.
I was talked into buying a Honeywell VisionPRO TH8320U1008 to replace the Totaline on zone-1. They said the Honeywell can be wired for any system. Anyway, I can't take it back and I can't get it to work properly.
The Totaline is wired as follows BLK-0/W2/B RED-R BRN-C BLU-Y/Y2 YL-Y1 GRN-G WHT-W/W1. A total of 7 wires hooked up.
The Honeywell only calls for 6 wires to be hooked up in the 2H/2C Heat Pump mode with [no auxiliary heat] I hooked the wires up as follows BLU-Y2 RED-R/RC Note, R+RC are jumpered. BLK-0/B YL-Y GRN-G BRN-C. I stored the WHT wire. Wired this way the heat pump would work, but would not control the reversing valve when when calling for heat.
The Florida Geo heat pump has the the reversing valve energized in the cooling mode.
Any help with this problem will be greatly appreciated.
On the honey well tstat you have to go into the installer set up and set the swithover valve for energized in cooling
Posted on Jan 19, 2012
The thermostat will to any temperature but will not shut off
Posted on Jan 28, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2018 | Honeywell Heating & Cooling
Sep 24, 2014 | Honeywell Th8320u1008 Visionpro Digital...
Apr 17, 2010 | Honeywell Programmable Thermostat Heater
Mar 04, 2010 | Heating & Cooling
Oct 25, 2009 | Honeywell Electronic Programmable...
Jan 21, 2009 | Heating & Cooling
Dec 23, 2008 | Honeywell Electronic Programmable...
Dec 15, 2008 | Honeywell Electronic Programmable...
1,385 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: