Question about Goodman Heating & Cooling
I just installed a GSC140421 using a coil CAPF 3642 . the problem is I can not get right pressure. low pressure is 80 psig high side pressure is 180 psig.
Hey there, the matching coil for your unit is a Model# CAPF4860C6A. The coil you have installed is a 13 seer where the condenser is a 14 seer. Myy guess at this point without being there is you have a hot house (80 psi suction) while eliminating more heat from the condenser (180 psi). I am also guessing you are using r-22? If you could post your super heat and subcool readings and if ou have a txv or fixed orifice (guessing txv?) I could help you pinpoint the problem.
Posted on Aug 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 19, 2016 | Vizio Televison & Video
Nov 17, 2015 | Refrigerators
May 01, 2014 | Goodman Heating & Cooling
Apr 08, 2014 | Cars & Trucks
Oct 13, 2012 | Acer Aspire 9300-3642 Notebook
Aug 29, 2012 | Goodman Manufacturing CAPF Cased...
Jul 17, 2011 | Goodman Heating & Cooling
Jul 09, 2011 | Heating & Cooling
Oct 06, 2010 | GE Monogram ZISS420NRSS 42" Built-In...
Sep 02, 2010 | Kenmore 72187 Air Conditioner
130 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: