Question about Coleman Mach III Air Conditioner
It's the mode switch contactors for the high setting just overview the wiring of the high cool or high fan contactors if it's not there check all leads for the high fan or high cool circuitry.
Posted on May 02, 2012
Check for proper voltage on high speed at the switch, if it's ok then you have an open winding on high speed an you need to replace the motor to correct the problem, however you can continue to use medium and low speed without replacing the motor.
Posted on Aug 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 01, 2014 | Haier HWR06XC7 Air Conditioner
Nov 21, 2013 | Hampton Bay Ceiling Fan. Chateau Deville...
are you saying the outdoor unit does run, then shuts off?
if not, there may be fuses in the disconnect
if so, it may be going out on low pressure, possibly high pressure....clean all coils, filter, blower wheel, inspect coil if possible
Jul 26, 2012 | Dometic Rooftop RV Air Conditioner
Apr 12, 2017 | Heating & Cooling
Aug 29, 2011 | Dometic Rooftop RV Air Conditioner
Jul 29, 2011 | Dometic Rooftop RV Air Conditioner
Feb 02, 2011 | Chrysler Sebring Cars & Trucks
Jan 18, 2011 | Hampton Bay Heating & Cooling
Feb 28, 2010 | 2001 Chevrolet Suburban
272 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: