Question about Pentair Minimax NT Heater
Troubleshot vaccum switch determined it was operational (Use Pentair's website for service instructions on the switch) Fan speed too slow due to worn out motor. Replacing blower assembly
Posted on Aug 02, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 04, 2014 | Pentair Minimax NT Heater
Mar 17, 2017 | Pool & Spa
Aug 24, 2011 | Pentair Minimax NT Heater
Jul 04, 2010 | Solar Rheem Gas Fired Pool & Spa Heater...
Aug 14, 2009 | Pentair MINIMAX NT TSI IGNITER
Apr 24, 2009 | Rinnai Toyostove Direct Vent Heater: Laser...
Feb 15, 2008 | Panasonic DP-C354 Copier
Jun 17, 2018 | Pool & Spa
1,460 people viewed this question
Usually answered in minutes!