Question about LG Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: lg split system air conditioner
Try sutting off the power to both units. This may reset the unit. Check out the service manual at LG website www.lgusa.com. Go to their support page and put the model number in. Remove and replace the batteries in the remote. If there is a communication error, the inside unit will display 3 flashes. If all else fails, call LG at 1-800-243-0000. Good Luck!
Posted on Aug 30, 2007
The model number would be on the right hand side of the outdoor unit and same on the indoor unit if it is a midwall split. If it is a flat cassette cieling type you may need to open the grill, which is simply two little levers either side of the grill, and the grill will swing open. Without the model number it is difficult to give accurate info. However, I can offer the following. One, check the condensate drain. You can just blow into the drain pipe from the outside and this sometimes clears clogged mud in the drainpan. Or two, error reading can also come from phase failure (in the case of a three phase unit) or power related problem. This can be solved by switching off the mains and then switching on again to reset. If you have a phase failure you would need an electrician to confirm that the power supply is good. Unless you have a volt meter.
Posted on Mar 04, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
Tips for a great answer:
Aug 21, 2017 | LG Heating & Cooling
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Jul 17, 2019 | LG Heating & Cooling
Jul 09, 2019 | LG Heating & Cooling
163 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: