Question about Goodman CLQ36AR49 Air Conditioner
Just turned the a/c (goodman) on this morning. it has been on approximately 8 hours and has only dropped from 89 degrees to 85 degrees.
Hot hot is it outside? is this a new system or somewhat older system? Do you know the S.E.E.R rating on the outside unit? Do you have any refrigeration gauges? CHeck outside and feel the bigger of the copper lines thats coming through the house. Does it feel warm? is it iced up? Does it feel somewhat cold? There can be several things. If its really hot outside then its probably not keeping up with the heatload inside the house. You can be low on Refrigerent charge. Evaporatore coils can be plugged and iced up.
Posted on Aug 01, 2009
It could be that the A/C has a slow leak from sitting without use (usually over the winter months) and you've lost some freon and the unit requires a recharge.
Another thing to check, but shouldn't really be causing this problem, unless really blocked is to make sure is to put in a new air filter. You need to change them every 2-3 months if using the better quality pleated ones during the heating and A/C seasons.
I'm betting on the A/C needing a charge of freon to get things cooling better. Unfortunatley, this will require a certified A/C tech, since you have to be trained and licensed to perform this type of service. (unless you have the recharging gauges and some freon available to you and know how to get the right amount into the unit.
Hope this helps, best regards!
Posted on Jul 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Hello Carlos Rojas, thank you for your post!
I understand that your Frigidaire refrigerator has been having some cooling issues. It sounds like a potential issue with your control panel or thermostat. I recommend performing a reset on your refrigerator which you can do by disconnecting the power cord for roughly ten minutes. If that does not help correct the issue I would advise to seek assistance from a professional technician for proper diagnosis and repair. I hope this information has been helpful. -Matt
Oct 11, 2014 | Frigidaire Refrigerators
Jul 07, 2017 | Goodman Heating & Cooling
Aug 13, 2010 | Goodman Heating & Cooling
Aug 16, 2009 | Goodman CKL36AR36 Air Conditioner
Jan 14, 2009 | Honeywell Electronic Programmable...
Jan 06, 2009 | Heating & Cooling
Nov 26, 2008 | Goodman Heating & Cooling
186 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: