Question about Haier HC48C1VAR Central Air Conditioner
Your problem is that your 13 seer outdoor unit is not compatible with your 10 seer indoor unit, even though the tonnage is the same. The metering device on 13 seer indoor units is different. Most 10 seer indoor units do not have an expansion valve. When you change from a 10 seer outdoor unit to a 13 seer outdoor unit, you must, at the very least, change the from a fixed-orfice metering device to an expansion valve.
Posted on Aug 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Amana Goodman R-410A Heat Pump Condenser 2...
Jul 18, 2014 | Rheem 14AJM49A01-RHLLHM4821JA 4 Ton 16...
Jul 17, 2014 | Haier HC30D2VAE Central Air Conditioner...
Feb 03, 2013 | Intertherm E3EB-017H Furnace 17Kw 2
May 02, 2011 | Heating & Cooling
Jul 12, 2010 | Goodman CKL36AR36 Air Conditioner
Jun 20, 2010 | Carrier 38CKC036 Air Conditioner
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 04, 2009 | Heating & Cooling
May 06, 2008 | Heating & Cooling
368 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: