Question about LG Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: LG Inverter A/C Unit LSJ092V-3
I would first check the condensate drain pipe. This can be done by blowing back into the drainpipe from outside. Not to worry it is not dirty or dangerous. Also make sure that your air filters are clean.
Posted on Mar 05, 2009
This may mean that the filters may need to be cleaned. According to service manual the unit has a "Serial reverse transfer
error at start up operation". Call fujitsu for service if the fault cannot be rectified.
I take the time to answer your questions, please rate me
Posted on Aug 28, 2009
Please specify the make and model of your unit.
If this is a LG inverter model.
The six flashes of the indoor unit light indicates a CH 06 alarm.
This alarm state indicates that the indoor unit pipe temperature sensor has measured a temperature out of range or the unit is protecting itself from this low temp state. Indoor unit coil temperature to low. Should it have reached a temperature of -5°C for longer that 30sec it will switch the machine off.
It could indicate that the unit refrigerant charge is too low or the sensor has gone out of calibration.
It should measure 5kΩ @ 25°C
Posted on Mar 22, 2010
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Oct 08, 2018 | Inverter Heating & Cooling
Jun 30, 2018 | LG Heating & Cooling
Jul 18, 2016 | Fujitsu Heating & Cooling
Dec 18, 2013 | Mitsubishi Heating & Cooling
Nov 26, 2013 | LG Heating & Cooling
Sep 24, 2017 | Fujitsu 18C1 Air Conditioner
Jun 16, 2011 | Heating & Cooling
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Mar 16, 2010 | LG Heating & Cooling
Jul 09, 2019 | LG Heating & Cooling
206 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: