Question about LG Heating & Cooling
Inverter compressor run all the time
it is internally controlled so that it only pumps the required amount of gas to keep the constant setting
so if you have a setting of 26 C and the ambient is 24 C the motor is running but the load on the compressor is reduced to zero== power savings
If on the other hand you have the setting on 18 C and the ambient temp is 35C then the compressor is under constant load and will run virtually all the time ==costly unit to run
Posted on Mar 30, 2018
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Good morning, I'm using Elekta window A/C 1.5 ton and I'm using this for almost three years and now there is eritating sound while the A/C is running. Could you please advise what is the problem?
Posted on Sep 19, 2009
SOURCE: best split ac 1.5 ton
I think you just have a faulty unit. Most of the mid wall split units have similar components and there are only cosmetic differences. Lg is strangely enough a good aircon. Personally i like Samsung .(Spares are easily available). You should concider who the best after sales service supplier is and go that way. (As stated, most units are similar in my oppinion.)
Posted on Sep 21, 2009
Yes they Do they are called Dual Zone Units. At http://www.paylessminisplit.com they are very helpful if you call them they can answer alot of questions about many brands of mini split air conditioners.
Posted on May 21, 2010
Easy: Turn the "fan" switch to on at the thermostat and see if the blower starts. If no start, check breaker at breaker box. Check service disconnect at or near the air handler. With the breaker and/or service disconnect OFF check the 3 or 5 amp fuse inside the top cover in the air handler.
Not so easy: (You must know what you are doing for this part or let an HVAC Tech do it for you) Open thermostat and firmly jump the Y and R terminals to see if you get the compressor to start for no more than 30 seconds. (don't do it more than once.) Jump the G and R terminals to see if you get the blower to start. If so, u have a bad thermostat. If not, check the transformer inside the same cover in air handler for proper voltage. (24V. Make sure you also get 220 on the opposite side of the transformer)
If the blower comes on, but the heat pump doesnt start, open the side cover of the heat pump, with the thermostat on cool, and the temp. setting as low as possible for at least 10 minutes see if the contactor is pulled in. If so, check the capacitor and see if it's blown out. Be super careful these systems operate with 220v and the amperes are enough to kill you if you make a simple mistake.
Posted on Aug 28, 2010
Tips for a great answer:
Mar 30, 2018 | LG Heating & Cooling
Aug 15, 2016 | LG Electronic Window Air Conditioner
Jan 19, 2011 | LG Heating & Cooling
Feb 17, 2010 | Samsung AW1293L Air Conditioner
Jan 22, 2010 | LG S5200 Cellular Phone
Sep 21, 2009 | LG Heating & Cooling
May 24, 2009 | Heating & Cooling
Jul 09, 2019 | LG Heating & Cooling
43 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: