Question about Generac Guardian 0A18010 - battery charger
Dont know if battery charger is connected properly, will not transfer back to utility after an outage
The transfer switch should transfer back to utility within about 30 sec. after utility is restored. While waiting for the transfer switch to switch back to utility volatge. Check for DC volatge across wires 23 and 194 in the transfer switch, if you have battery voltage(12-13.5 VDC) then you you probably have a stuck relay on the PC board in the generator. The board needs to be replaced. If you don't have battery voltage across these terminals then your problem is actually in the transfer switch.
Posted on Dec 26, 2009
Does the unit operate normally when there is an outtage? Don't know your system,but, guessing the re transfer delay timer is not working.
Posted on Aug 01, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 12, 2017 | Intermatic Hardware & Accessories
Dec 13, 2014 | Kohler Electrical Supplies
Aug 20, 2014 | Electrical Supplies
Oct 08, 2012 | Generac Guardian 200 Amp Transfer Switch...
Nov 01, 2009 | Guardian Electrical Supplies
Sep 08, 2009 | Generac Guardian 100 Amp Transfer Switch...
Sep 04, 2009 | Generac Guardian 100 Amp Transfer Switch...
Sep 02, 2009 | Generac Guardian 200 Amp Transfer Switch...
Jul 01, 2009 | Generac Guardian 200 Amp Transfer Switch...
274 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: