Question about Heating & Cooling
There may be a wiring diagram pasted inside the furnace housing. If not, request the wiring diagram directly from the manufacturer/distributor.
Posted on Mar 12, 2018
Testimonial: "TYVM yes wiring diagram was inside but unreadable.The company was Holly-General Co. division of the Siegler Corp. Pasadena Ca not in business anymo"
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Posted on Dec 13, 2007
I have a forced air gas furnace and water is leaking from just above the area where the hose is attached. I removed the cover but cannot figure this out. It only leaks (a lot of water) when the furnace is running. Please help asap!!! Tthanks so much, Dianne
Posted on Jan 03, 2010
Tips for a great answer:
Dec 18, 2016 | Heating & Cooling
Apr 22, 2017 | Dometic Rooftop RV Air Conditioner
Dec 21, 2012 | Heating & Cooling
Dec 14, 2012 | Coleman 7990-319p Evcon Gas Furnace...
Oct 08, 2012 | Heating & Cooling
May 02, 2011 | Heating & Cooling
You need to find out if the problem is in the T-stat, T-stat wire or in the furnace you can do this in a few easy steps
Step 1- Unwire the low voltage from the furnace. Then turn the power back on and see if the blower comes on if it does then the problem is in the furnace and you will need to troubleshoot the furnace (see bottom of page for troubleshooting furnace) if it does not then proceed to step 2
Step 2- Wire the low voltage back up to the furnace (follow the wiring diagram below). And unwire the T-stat, make sure that no wires are touching each other, then turn the power back on to the furnace, if the blower starts then you have a short in the T-stat wire and you will need to pull a new wire. If it does not then proceed to step 3
Step 3- Turn the power back off at the furnace and wire the T-stat back up (follow the wiring diagram below). Turn the T-stat to auto heat 90 if the heat does not start but the blower just runs then you need to replace the T-stat.
Nov 24, 2010 | Comfort-Aire Heating & Cooling
Mar 29, 2010 | LG LWHD1800R Wall/Window Air Conditioner
Feb 22, 2010 | Coleman Propane Forced Air Heater...
Jan 17, 2019 | Honeywell Heating & Cooling
198 people viewed this question
Usually answered in minutes!