Question about Heating & Cooling
The condensor fan had purple (went to the run cap) and black and orange when to contactor. Now I have Purple, Browm and a Gray brown stripe. PLease advise how to usue these wire to the run CAp (fan) and the other two wire to the contactor
Brown and grrey brown strip go to seperate capacitor. but you can tale off the gray/brown and use it by putting it on the capacitor where the other wire come off. Russ
Posted on Jul 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 02, 2013 | Dryers
Apr 11, 2013 | Heating & Cooling
May 16, 2011 | Heating & Cooling
Dec 08, 2010 | Heating & Cooling
Aug 11, 2010 | Heating & Cooling
May 27, 2010 | Dayton Permanent Split Capacitor Motor Fan
Hello. The most common configuration is: L - Orange, 1 - Black, 2 - Yellow, 3 - Purple
. Here's a link to some troubleshooting advice: http://www.ceiling-fans-n-more.com/ceiling-fan-pullchain-replacement-and-repair.php and a link to diagrams: http://www.hurontel.on.ca/~taitg/pages/cfan.html
Hope this helps, and don
Apr 15, 2010 | Speed Ceiling Fan 3-speed Switch By...
May 02, 2009 | Westinghouse Electric Westinghouse...
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
Aug 14, 2008 | Carrier Heating & Cooling
98 people viewed this question
Usually answered in minutes!