Question about Heating & Cooling
I have an Intertherm S3QA042K that has an intermittent problem. Once the compressor runs and cools house to set temp and cycles off the compressor won't restart when the thermostat calls for cooling again. I've checked the run cap and it checks fine, replaced contactor, thermostat, and wiring from outside unit to inside unit. I can switch off the breaker to the compressor wait for an hour or so and then switch it back on and it starts and cools again to set temp. Problem returns after next cycle or so where the compressor won't restart. The contactor clicks and I'm getting 24VAC . Shut off breaker, wait, and reset breaker and it runs again
Sounds like rotor lock. (intertherm sold a hard start kit under the name "soft start" kit for high temperature areas) If you hear your bus bar humming in the electrical panel when it attempts to start this is a good indication.
Posted on Jan 26, 2011
You probably need a hard-start kit. A hard-start kit connects to the run capacitor and provides a starting boost for your compressor. If you install a hard-start kit, monitor your a/c for a while because it is possible that the bearings in the compressor are going bad.
Posted on Jul 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 07, 2016 | Intertherm Heating & Cooling
Jun 08, 2015 | Intertherm Heating & Cooling
Sep 11, 2013 | Intertherm Heating & Cooling
Jun 15, 2012 | True GDM-10 Refrigerator
Jul 15, 2010 | Goodman CPLE24-1 Air Conditioner
Apr 19, 2010 | Intertherm P3RA-030K Air Conditioner
Jun 25, 2008 | Intertherm Heating & Cooling
406 people viewed this question
Usually answered in minutes!