Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
I'm not sure my model number because i can't find it as escribed by the search function (why this company can't simply list the model # in an obvious place is beyond me). I see some mechanically printed numbers along with 'Made In Taiwain' that read T7300F2184, this isn't listed as a model number anywhere though..
Anyways, the AC isn't working (or anything really), but its 85°F and i'm sweating just typing. I set all the programs to begin at 1 or noon and put temp to 65°F but it doesn't do anyhing (It's been 5 days now). If I press temp occupied button it says 'override', if I press the continuous unoccupied button it says 'hold' . Sometimes it won't let me change the Fan option but other times I can only cycle between on and auto (I swear there used to be an 'off'). The fan seems to be on very midly in a back room but it's not cold air (and it might even be hot, I can't tell cause its so damned hot in here).
If I select a system setting it doesn't do whatever function it's told and sometimes it shows the little snowflake icon and sometimes it says wait indefinitely.
Sounds like the tstat, obviously, isn't responding. A sure check is to bypass the tstat. Turn power off to airhandler and remove cover. Remove red, green and yellow wires and wire nut/ twist together. Turn machine on and see what you get. If inside and outside turns on...bad tstat OR just not setup properly. EVEN THE PROFESSIONALS READ THE INSTRUCTIONS THESE DAYS!!
Posted on Mar 04, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Access the installer setup menu (You will need the installation manual from the t'stat to do this) and turn off the "intelligent recovery" feature. This feature turns the equipment on in order to bring the conditioned area up to temp at the set time. Or you could set the "wake time" to 6:50!!!
Posted on Dec 16, 2008
Joss sounds like the anticipator setting on thermostat i would replace it with a digital it will be more actturat . The furnace has to go over temp setting to turn off
Posted on Jan 18, 2009
Most thermostats use a six volt transformer for a power source, similar to a door bell, you can tell if yours does by looking at the wires that are attached to the thermostat.
The wires will be thin with just a single strand if you have these wires then you have a transformer, try and find the transformer (good luck) test it with a voltmeter if it fails the test that's it, if not, call the man. Probably it though.
Posted on Feb 15, 2009
IN MOST PROGRAMMABLE STATS THERE IS A FACTORY DEFAULT PROGRAM.IT COULD BE
RUNNING IN THAT MODE.FIRST,CHANGE THE BATTERIES IN THE STAT.ALSO,THEY HAVE A
RESET BUTTON ON THE CIRCUIT BOARD.TRY THAT.AND,BY THE WAY,YOU ARE NOT SAVING
ANY MONEY BY DOING A TEMP SETBACK.THE HEAT SYSTEM WILL USE JUST AS MUCH
FUEL EVERYDAY TO RECOVER THE LOST HEAT DURING THE SETBACK PERIOD.ALSO,THE STAT COULD JUST BE BAD.
Posted on Mar 07, 2009
Tips for a great answer:
Jan 28, 2016 | Televison & Video
Aug 22, 2012 | Frigidaire Dishwashers
Sep 12, 2011 | Whirlpool Water Heaters
Oct 02, 2010 | Televison & Video
Aug 05, 2010 | MSI P4M900M-L Motherboard
Aug 10, 2009 | RIM BlackBerry Storm 9530 Smartphone
Jun 18, 2009 | Computers & Internet
Jan 05, 2009 | Simply Media Simply Money & Personal...
Nov 17, 2008 | Brother GX-6750 Typewriter
43 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: