Question about Amana Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: E1 error code
highly annoying issue error code E1. After hours
of fan operation, the error code E1 will appear on the seven segment
LED temperature display. This error code is intended as a reminder for
the user to clean the air filter. However, because the procedure
outlined in the user manual does not clear this error code as
indicated, and the appliance has a nonvolatile memory that cannot be
reset by simply unplugging it, the user of the appliance will become
mightily frustrated, standing in potentially sweltering heat watching
the appliance repeatedly shut down in the midst of operation with the
"E1" display flashing.
Believe it or not, that is what it does: if you unplug it to remove the
"E1" code from the display, and plug it back in and re-start it, it
will simply run for anywhere from a few minutes to a few hours, and
then merrily shut down again with the same flashing "E1" code.
So you will come home to a hot bedroom, living room, etc. unexpectedly,
and you will NOT be amused, as I was not.
Many people at this point, having put the manual under the canary or
some such, will simply return the unit and never buy another Sharp air
conditioner. But for the tech-savvy and search-adept, I offer the
following procedure to clear the nefarious E1 indication, and obtain
1. Power down the air conditioner using the "power" button on the front
2. Unplug the air conditioner from the wall socket.
3. Hold the front panel "power" button down and plug the air
conditioner in. Continue to hold the power button down as the machine
goes through a brief test sequence (fan & compressor each come on
briefly, etc). There is a "beep" sound at the end of the test sequence,
and the machine will be off. At this point, you can release the power
4. Unplug the air conditioner.
5. Plug the air conditioner back in.
6. Congratulations! You should now be able to operate the air
conditioner normally for another 720 hours, but only if you followed
the instructions above EXACTLY.
Was this solution helpful? Show your Appreciation by rating it.
Thanks for using fixya support..You have a wonderful day
Posted on Jun 05, 2008
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
SOURCE: Amana PTAC
I know this is late but I had to add a solution to this problem since I had the exact same problem and was able to solve it. The probelm is not your control board. On these units, the heat pump compressor will not kick in unless the temperature you set on the control panel is within 2-1/4 degrees (or 4 degrees depending on your unit model. Otherwise, the unit locks out the compressor until the electric heat coil bring the indoor temperature up to that level - and then will switch the compressor back on for heat pump operation. So the problem is not the control panel or the compressor, it the electric heat coil. The coil has two manual limit switches on it that may be tripped and should be checked. The coil can be easily accessed by shutting down the power, removing 4 screws around the air outlet, pushing the screen up and sliding the panel out the top. The power wires can remain in place while the limit switches are reset. Hope it works.
Posted on Nov 06, 2011
Tips for a great answer:
Sep 11, 2016 | Amana Heating & Cooling
Aug 21, 2015 | Amana Heating & Cooling
Feb 14, 2013 | Amana PTC093B50AJ Electric Heat Air...
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Aug 31, 2012 | Amana PTH123B50AJ Heat Pump,12000BTU,...
May 14, 2011 | Amana PTH123B25AJ Heat Pump Air...
Jan 19, 2011 | Heating & Cooling
Sep 26, 2010 | Amana Heating & Cooling
Jan 23, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Jul 04, 2018 | Amana Heating & Cooling
1,034 people viewed this question
Usually answered in minutes!