Question about Heating & Cooling
No air is coming out
Shut the power off to the unit, spin the fan blade to see if it spins freely. If it doesn't spin freely, (there appears to be a little drag when you spin it),the bearings are bad, if it does spin freely, then try moving the motor shaft from side to side if there’s any play in the shaft side to side then the bearings are worn and motor needs replaced. Then, check the capacitor, if it’s bulging even slightly, the capacitor is bad and needs replaced. Most of the time people replace the capacitor if motor seems ok. If capacitor is ok, turn power on to see if the motor is getting the proper voltage, if it is and not trying to run, then the windings are probably open, the motor's bad and needs replaced.
Posted on Aug 25, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2015 | Whirlpool Refrigerators
Aug 07, 2013 | Heating & Cooling
May 28, 2011 | Heating & Cooling
Aug 25, 2010 | Goodman CLT36AER36 Air Conditioner
May 18, 2010 | Heating & Cooling
Dec 31, 2009 | Superior Lennox Blower Thermal Sensor -...
Jul 15, 2009 | Refrigerators
Jun 16, 2009 | Heating & Cooling
92 people viewed this question
Usually answered in minutes!