Question about Goodman CLQ36AR49 Air Conditioner
Sounds like it could be an issues with your defrost control board this device allows the fan to shut off during the defrost cycle of operation in cooling the relay is in the closed position allowing power to the fan this relay on the board could have bad contacts a highly suggest calling a contractor that specializes in heat pumps and would also question why a part was replaced and you still have the same problem did they credit you any money back?
Posted on Jul 28, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2013 | Goodman Manufacturing Goodman AEPF313716...
Aug 27, 2012 | Heating & Cooling
Jun 27, 2017 | Heating & Cooling
Sep 14, 2011 | Heating & Cooling
Feb 17, 2011 | Heating & Cooling
Jan 24, 2011 | Goodman Heating & Cooling
Sep 19, 2009 | Goodman CKL36AR36 Air Conditioner
Apr 08, 2009 | Goodman Heating & Cooling
Dec 06, 2008 | Goodman CLQ36AR49 Air Conditioner
Apr 04, 2008 | Goodman CKL24AR24 Air Conditioner
218 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: