Question about Heating & Cooling
There could be excessive heat developing causing internal overload protectors to open when it has reached that temperature. This could be due to bearing or winding problems with the compressor. Another possibility is the capacitor if it is not operating correctly can cause problems with the heat or high amp draw at start up.Measure the amps on the compressor for about thirty minutes. If the amps keep rising the compressor is the problem. Check the capacitor. If it is balloned out at the top replace it, check to see the resistenance reading rises and falls when the probes are connected. Any thing different replace scott Buehler
Posted on Jul 28, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 15, 2015 | Refrigerators
Jul 30, 2014 | Goodman Manufacturing Goodman GSX130481...
Jul 06, 2014 | Goodman CLQ36AR49 Air Conditioner
Sep 27, 2012 | Goodman Manufacturing Goodman GSC130301...
May 13, 2011 | Goodman CLQ36AR49 Air Conditioner
Jul 01, 2010 | Goodman CLQ36AR49 Air Conditioner
Dec 20, 2009 | Goodman GDS80904BNA Open Flame Heater
Jul 08, 2009 | Goodman Heating & Cooling
Dec 26, 2008 | Maytag MTB1891AR Top Freezer Refrigerator
57 people viewed this question
Usually answered in minutes!