Question about Eaton Powerware® 9125 UPS System
Powerware 9125 3000VA UPS will not power up long enough to make it through the self test. I am set up with 2 EBM modules as well as the internal batteries. Have been sitting for nearly two years in a dirty warehouse, although the inside electronics are very very clean and I see no fuses open. Obviously the batteries might be shot, but I have no other components to really test that, however, I would think that the Line AC light would still turn and blink on when I got Utility power. However it doesn't. Hit the power on button and it tries to boot, but turns off and immediately tries to reboot. On the off chance it does work the batteries must be shot because it never reaches battery mode. Just shuts off. Any ideas? Thanks in advance for taking the time!
Most modern ups units will not start at all without the batt, so disconnect the extra packs beg, borrow some new or old good batt blocs same spec as the original internal ones, as this is just a test any set of batts that is just ok will do.
fit them to the ups unit and see if it will start. if it will then you will need to replace all the batt blocs in the whole system.
If it does not start then the ups is faulty.
If you are not happy fitting /working with batteries then get a tech to do this work for you, batteries are very dangerous, they are always live and need to be handled with care at all times.
Hope this helps, thanks for asking FixYa
Posted on Sep 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
After you replaced the batteries did you perform a manual battery test?
If not do so.
Posted on Mar 03, 2009
SOURCE: APC Smart UPS 3000VA - Dead UPS
ok how long you brought the ups and how long you had not start the the ups usaully ups is power dead change the battery and try to power up it should work be sure that all connection is connect properly before power up the ups.. if the ups doest work that will be the mainboard problem you hav to call for vedor to repair the unit.. yes these fuse for the ups but it unlikely to be blown so should worry of the fuse it self.. change of battery come with different spefc for the ups.. eg su3000rmi3u, sua3000rmi3u, su3000rmxl3u --- battery replacement is 8 pcs of 12v 7ah. sua3000rmi2u-- 6 pcs of 12v 7ah or 8 pcs 12v 5ah. su3000rminet-- 4 pcs 12v 17ah,
Posted on Mar 28, 2009
it is possible the bypass alarm is flashing because the i/p and o/p are not within range to switch without a break.
they need to be nearly equal in volts and freq so when the ups switches the ups o/p is continuous.
you should be able to check this with your ups software.
Posted on Sep 16, 2009
Tips for a great answer:
Sep 25, 2014 | Eaton Powerware® 9120 UPS System
Aug 25, 2014 | Eaton Powerware Pulsar M 3000 3000VA...
Jan 17, 2014 | APC Symmetra PX SY64K160H UPS System
Nov 16, 2013 | Powerware 9120 UPS System
Mar 01, 2011 | Powerware 9125 UPS System
Nov 27, 2010 | Powerware Eaton PW9130 3000VA Tower UPS ...
Mar 11, 2010 | Computers & Internet
Dec 11, 2009 | Computers & Internet
866 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: