Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: no heating from Mr slim
P8 refers to outdoor protection device activation usually caused by low gas charge or blocked condenser coil. any good a/c company can resolve this for you. however please note that if it is gas related a pressure test must be carried out to determine where that potential leak may be and that can be very costly.
Posted on Nov 14, 2007
HOW TO WORK THE HEATING AND COOLING CONTROL PANEL
- PRESS THE SWITCH ONCE IT OPERATES "COOL"
- PRESS THE SWITCH AGAIN IT OPERATES "HEAT"
- PRESS THE SWITCH ONCE AGAIN IT STOPS.
Posted on Mar 05, 2008
no sir gary,
the water would not go to the drain pan if you install it vertically.
water would just drop anywhere and would ruin a lot of things...
tnx 4 using fixya,
Posted on Sep 13, 2008
Tips for a great answer:
Feb 05, 2016 | Mitsubishi Electric Mr Slim E12C26426...
May 27, 2014 | MR SLIM Split-ductless: Mitsubishi...
May 03, 2017 | Heating & Cooling
Aug 10, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Sep 13, 2008 | Mitsubishi Mr. Slim MXZ30TN Air...
Nov 13, 2007 | Mitsubishi Mr. Slim MXZ30TN Air...
41 people viewed this question
Usually answered in minutes!